The controller TR1B is designed to regulate and control the room-temperature individually set by the resident. The dew point surveillance, which is important to protect the cooling ceiling against damage resulting from condensation, is realised by connecting a dew point sensor.
The controller TR1B (on‐wall mounting) has an exit to actuate a valve and is switchable between heating or cooling.
Clina Room Temperature Controllers are equipped with a connection for Clina Dew Point Sensors. The actual operating mode (cooling / heating / danger of dew point) is indicated by light‐emitting diodes.
The room temperature is controlled via a simple 2‐point‐control mode (ON/OFF). The temperature controller records the room temperature and activates the zone valve with actuator via a control signal . As a result of the low level water content and the spreading of 2‐4 K, a modulating control 0-10 V is not necessary. This type of room temperature control is preferentially used for cooling and also heating purposes with the capillary tube system.
|Description||room temperature controller TR1B|
|Operating voltage||24 VAC/50 Hz, 24 VDC|
|Control range||13‐29 °C|
|Function||cooling or heating
with switchover ECO‐function